The mixed-bed cartridge desaliQ:BA is a compact mixed-bed ion exchanger system for the full demineralisation of water of drinking water quality or for the residual demineralisation of partially demineralised water, e.g. for the initial filling or make-up water feed of heating systems. The stainless steel cartridge is filled with high-quality mixed-bed resin that can be regenerated again by a specialist. The mixed-bed cartridge features an internal distribution system, a plastic ring with carrying handles, a plastic foot and an oval, clip-lock-type lid for easy replacement of the resin, a flow stabiliser and a deaeration valve. Its nominal connection diameter is ¾", the maximum operating pressure is 10 bar and the maximum water temperature is 80 °C.
Please note local installation directives, general guidelines and technical specifications. The installation site must be accessible for maintenance work, flood and frost-proof and ensure that the system is protected from chemicals, dyes, solvents and vapours. The ambient temperature as well as the radiation temperature next to the system must not exceed 40 °C. The installation room must have a floor drain. The raw water must comply with the German Drinking Water Ordinance. In accordance with DIN EN 1717, a system separator (e.g. GENO®-DK 2-Mini) must be installed upstream of the Mixed-bed cartridge desaliQ:BA if the GENO-therm® filling device is not used. Installing a drinking water filter (e.g. BOXER® KD) upstream of the Mixed-bed cartridge desaliQ:BA further increases the operating safety of the mixed-bed ion exchanger system.
Mixed-bed cartridge desaliQ:BA are supplied full. The hydraulic connection is achieved via the GENO-therm® hose set, which can be ordered as an optional extra.
For further information on installation requirements and accessories, as well as technical details, see the product data sheet, which is available to download.