The space-saving reverse osmosis system GENO®-OSMO-X is used to demineralise drinking water. The generated permeate is used in medical engineering or in the food and beverage industry. Via a fine filter incl. pressure reducer, the water reaches the high-pressure pump via the inlet solenoid valve. The pump speed can be set using a frequency converter so that the system-specific permeate capacity is achieved. The permeate recovery of the GENO®-OSMO-X is up to 80%. The GENO®-OSMO-X has an energy-saving mode of operation, can be connected to conventional BUS systems and is equipped with integrated data logging and a multilingual touch panel. AVRO technology can be used in preparation for the reverse osmosis.
The installation site must offer adequate space. The system may only be installed with the left side (pressure pipes) flush to a wall. It is important to observe an adequate distance (> 50 cm) in front of, behind and to the right of the system for installation and service work. Provide a foundation of a sufficient size and adequate load-bearing capacity. The required connections must be provided prior to the installation work. The installation of a reverse osmosis system represents a major intervention in the drinking water system. Therefore, only authorised experts may install such systems. The local installation directives and general regulations must be observed. The following must be installed upstream: Drinking water filter (e.g. BOXER®), system separator, water softener and activated carbon filter.
For further information on installation requirements and accessories, as well as technical details, see the product data sheet, which is available to download.